Color steel plate is widely used in construction, home appliances, transportation and other industries. For the construction industry, it is mainly used in steel structure workshop, airport, workshop, activity room, box room, purification workshop, warehouse, freezing and other industrial and commercial buildings, such as roof walls and doors, while less color steel plate is used in civil buildings. The installation of color steel plate is very technical. Companies without experience don't know how to install color steel plate to meet the requirements. Here Jinan color steel introduces the installation requirements of color steel plate according to the experience of many years of construction teachers, hoping to help you.
Installation requirements of color steel plate:
1、 Site verification
After the first treatment on the clean ground, the equipment should be positioned. According to the equipment positioning and design drawings, set out and position the partition wall to determine whether the site size conflicts with the drawing size and equipment location;
2. Verify the level of the ground to see if the fluctuation is large, and whether it is necessary to level the bottom of the color steel plate wall as a whole.
2、 Installation requirements
1. Internal and external arc fixation: the connection with color steel plate must be tight, the external arc column shall not be connected, the internal arc connection points shall not be dislocated, and the gap shall be tight.
2. There must be three tail drilling screws between each roof and the enclosure, and a pull screw at the upper and lower joints between the enclosure and the vertical plate. The plate joints must be vertical while the construction is in progress;
3. Fixation of T-shaped lifting beam: the lifting code shall be positioned along the setting out position, and the spacing shall not exceed 1.20m. When fixing the T-shaped beam and the connecting color steel plate, the angle aluminum or angle iron must be used to compress the T-shaped beam, and no gap shall be left. The pressing solid must be on the joint of two color steel plates;
4. Fixing of channel aluminum: before fixing the channel aluminum, the setting out and positioning must be carried out, and the deviation shall not exceed 5mm. The channel aluminum shall be fixed with m5x30 core pulling aluminum nail, and the indirect distance shall not exceed 300 mm. Double pulling nails shall be set at the position with door opening, and the interval shall not exceed 50 mm;
5. Installation of air outlet: the installation of air outlet on the ceiling shall be carried out according to the drawing, avoiding T-beam. The air outlet and return outlet on the wall shall be installed 200 mm above the ground;
6. Appearance requirements: the overall installation shall be straight and beautiful, without collision and scratch marks, the protective film can be torn only after reaching the surface, the plate seam connection shall be smooth, the plate seam spacing shall be 3-4mm, and the gluing shall be full seam and straight, without gaps;
7.门窗安装：门窗的安装位置和开启方向按图纸要求而定，单开门尽量在同一块彩钢板上，双 开门的中 心线尽量在板缝连接处，以便切下的彩钢板做门板，门窗的型材连接需严密，不能有缝隙，整体门拐留置尺寸一定统一；
7. Installation of doors and windows: the installation position and opening direction of doors and windows shall be determined according to the requirements of the drawing. The single door shall be on the same color steel plate as far as possible, and the center line of double door shall be at the joint of plate seam as far as possible, so that the cut color steel plate can be used as the door plate. The profile connection of doors and windows shall be tight without gaps, and the overall size of the door shall be uniform;
The above are the installation requirements and specifications of Jinan color steel plate, and some precautions of both site and installation are sorted out. If you want to know more wonderful content, you can pay attention to it directly http://www.jnhxtcg.com